c) For each nonmetered Bldg Type and Group identified
on the Table 3 form, find the corresponding EUI in the Electric
Misc. EUI column in Table B-1 of Appendix B and enter that value
on the Table 3 form.
d) Similarly, find the appropriate DHW EUI (if
electric) and enter it on Table 3 form.
e) If the building is cooled, find the appropriate
CDD(65) factor in Table B-1 and enter it on the Table 3 form
along with the appropriate CDD(65) value. If it is a family
housing building type, also add the appropriate WBH factor and
f) If the building is heated electrically, find the
appropriate Electric Heat factor in Table B-1 and enter it on the
Table 3 form along with the appropriate HDD(65) value.
Sum the EUI portions to derive a total building
h) Calculate the total consumption for each building
type using the appropriate total area values. Total consumption
for nonmetered buildings can be estimated by totaling all
building type totals.
Metered Building Electric Data