25 May 2005
Change 1, 22 February 2006
Change 2, 4 December 2006
For Fire Protection systems only, provide manufacturer's data sheets instead of
prescriptive specifications, for the suppression systems, the detection and alarm
systems, firestopping, and spray-applied fireproofing. In exception, and in addition,
submit prescriptive specifications when included as part of the RFP.
Project Information Form (PIF).
For Design-Bid-Build projects and Design-Build RFP development, provide a PIF for the
project. The PIF is available on the Construction Criteria Base (CCB) at the Whole
Building Design Guide located at www.wbdg.org\ccb under the Specifications Library,
and then, NAVFAC Specifications.
Provide separate updated interior and exterior color boards indicating all proposed
material and color selections.
Revise calculations as required to reflect resolution of all previous government review
comments. Provide design analysis that is 100% complete. Provide calculations for
each discipline in addition to the following detailed requirements.
Submit calculations to support the plumbing and mechanical systems and the major
equipment comprising those systems. Update the energy analysis, provided at the
Design Development phase, with the equipment efficiencies scheduled on the drawings.
Provide updated Calculations from previous submittal to substantiate design level
shown, including the following, as applicable.
Motor Starting/Flicker Analysis.
Sag, Tension, and Guying Analysis.
Manhole Design Calculations.
Cable Pulling Tension Calculations.
Cathodic Protection Calculations.
CATV Network Loss Calculations.